CEI EN (Tab. 9). Current capacity: CEI UNEL /1 – CEI UNEL Rated voltage Uo/U: 0,6/1 kV. Max. voltage: 1,2 kV. Testing voltage: 4 kV. DC resistance: according to, CEI EN (Tab. 9). Current capacity: CEI UNEL /1 – CEI UNEL Rated voltage Uo/U: 0,6/1 kV. Max. voltage: 1,2 kV. T R ATOS FTG10OM/1 kV 4 X 2 5 CEI III CEI F2 UNEL /1. UNEL CEI / EN CEI EN EN
|Published (Last):||9 October 2011|
|PDF File Size:||3.54 Mb|
|ePub File Size:||1.41 Mb|
|Price:||Free* [*Free Regsitration Required]|
Applies to oil-resistant flexible cables with insulation and PVC sheathing. Production unit 2, 3 and 4 Brendola VI: EN Specifies the ageing conditions and procedures to be used for deriving thermal endurance characteristics of materials. Describes the procedure for determining the potential corrosivity of the gases emitted during the combustion of materials taken from electric cable constructions by measuring the acidity pH and the conductivity of an aqueous solution resulting from the gases emitted during combustion.
Specifies the electric cable designation symbols for energy, signal and control for national cables. EN Specifies the equipment and method of test for the resistance to fire of cables having a diameter greater than 20 mm.
CEI Specifies the construction requirements, testing methods and requirements for fire resistant cables, for operating voltages from 1kV up to 3 kV. Cross-linked compound with low smoke, toxic and corrosive gas emission.
Type 1 and Type 2. UNEL Specifies the markings and classification of cables in relation to fire. EN Describes the construction requirements, methods and test requirements for insulated and sheathed cables in the LS0H crosslinked compound.
Describes the construction and size requirements of the 0.
Specifies the continuous current capacities for open air installation of power cables with operating voltages up to 1, V AC and 1, V DC. Method with mechanical shock. Direct contact Send an email directly to our offices General information Sales Purchasing department.
C Specifies the test procedure for the assessment of flame spread of bundled cables, with non-metallic material of 1. UNEL Specifies the identification of cores in electric cables. Metallic coatings shielding and armouring.
The cables are intended for interconnection of the production machines. Specifies the test procedure and requirements for the assessment of the vertical flame propagation on single cables.
FG7OH2M1 0,6/1 kV CEI – CEI UNEL /
Specifies the test procedure for the determination of degree of acidity corrosivity of gases, released during combustion of materials from cables, by measuring Ph and conductivity. Describes the construction and size requirements of 0. CEI Provides guidance on using electric cables with an operating voltage up to 0.
Underground lines from 1 to 45 kV. Describes the construction and size requirements of cables for signalling and control, type FG7OM The cables are for connecting domestic appliances to the fixed power supply. Via Orna, 35 Specifies the markings and classification of cables in relation to fire. Reaction to fire class: EN Describes the testing procedure for determining the smoke density emitted by the cables subjected to combustion. CEI Specifies the general requirements for high modulus EPR insulated cables for distribution, with operating voltage of 0.
Logistics unit Brendola VI: Polyolefin-based thermoplastic with low smoke, toxic and corrosive gases emissions. Corporate info La Triveneta Cavi s. Single-core cables with flexible conductors for fixed wiring. Specifies the test procedure for the assessment of flame spread of bundled cables, with non-metallic material of 1.
FG7OH2M1 0,6/1 kV CEI 20-13 – CEI UNEL 35382/35384
Single-core without sheathing and with flexible conductors. SinceLa Triveneta Cavi has been one of the major players within the European market for low- and medium-voltage cables for various sectors industry, home use, power distribution, renewable technologies. CEI Specifies the calculation of the current rating of power cables in steady condition. See the dei-unel of positions currently available and fill out the job application form.
Specifies the continuous current capacity for open air and underground installation of medium voltage power cables. EN Specifies the methods for marking by inscription for the identification of cores of electric cables. Specifies the technical characteristics and test requirements for insulation and sheath compounds of power and signalling cables. Specifies the ageing conditions and procedures to be used for deriving thermal endurance characteristics of materials.
Multi-core with ce-iunel conductors for fixed wiring, with or without shielding. Shielded and unshielded types are included.
Specifies the construction requirements, testing methods and requirements for fire resistant cables, for operating voltages from 1kV up to 3 kV.
Specifies the general requirements for high modulus EPR insulated cables for distribution, with operating voltage of 0.