IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. 5. Voltages limited by arresters. Arrester power frequency witstand voltage. Resulting . An allowance of at least 5% (IEC ) is recommended. With this.
|Published (Last):||20 April 2006|
|PDF File Size:||15.6 Mb|
|ePub File Size:||6.82 Mb|
|Price:||Free* [*Free Regsitration Required]|
Please note that the selected standard is invalid.
What is a standard? Selection and application recommendations Article no: Subscribe on standards with our subscription service.
Shopping cart Close cart 0, foreach: SS Valve type surge arresters – Terminology. This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced uec IEC It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
Contact us svenska Login. Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to when selecting the type and rating.
Valid Buy this standard. Your shopping cart is empty.
IEC | IEC Webstore
This third edition cancels and replaces the second edition published in Report error on page. Typical maximum residual voltages are given in Annex F. TC 37 – Surge arresters rss.
Do you need a multi-user copy? Surge arresters – Part 5: We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. Fuses and other overcurrent protection devices Substations, surge arresters.
IEC RLV | IEC Webstore
When you use our service you can be assured the latest editions and easy access. Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. The standard is now in your shopping cart.
Selection and application recommendations. This edition constitutes a isc revision. The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition.
Sustainable Development Goals and standardisation, how do they connect? Subscribe on standards – Read more.
IEC System of Conformity Assessment Schemes
The following test report forms are related: The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued.
Message to your colleague. Read more about SIS Subscriptions. Our prices are in Swiss francs CHF. Selection and application recommendations Status: It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC In Annex J, some aspects regarding the old type of SiC gapped arresters are iwc.